2. Dynamic type LIM leakage current display:
In isolated panels, there is a device called LIM (Line Isolation Monitor) whose task is to constantly check line isolation. In case of errors and problems in the system, it calculates the next passing current and if this current is higher than the defined threshold for the system, it warns the operator visually and audio-visually.
Its unit is mA, which includes the following:
Power factor (P.F) display
Audible and visual leakage current warning display
Unauthorized voltage warning display audio and visual
Audio and visual trans overload warning display
Audio and visual display of non-standard temperature warning
Sending information over the Ethernet network in order to monitor the work of LIMs graphically and numerically on the computer
Electrical sockets that are responsible for supplying electricity to the devices, these sockets have an earth system, and the earth socket is also used to connect the earth to the desired devices in the operating room.
4. X-ray outlet:
It is a socket that can be installed in different parts of the hospital, including the operating room, surgery room, and delivery room, and it is used to connect the radiology device in the respective rooms. Due to its design and construction, the X-ray outlet can carry electricity up to 250 volts.
In each operating room, there is a central earthing unit, whose efficiency is such that the central earthing system is transferred to this device, and then the central earthing unit transfers it to all parts of the operating room, for devices and sockets that require earthing. have.
6. LIM Remote:
When the isolation device has a fault, the LIM of the device warns and then this warning is transferred to the side alarms to notify the hospital staff to fix the problem. Usually, side alarms are installed in two places, the operating room and the nursing station.